This segment will show you how to mount an ACC in both wall and pedestal mount configurations. Learn where to locate your ACC commercial controller based where the power supply is available, proximity to field and sensor wires, communications, possible tree root growth and water collection areas.
Appropriate conduit size and configurations for your controller wiring will be covered as well as correct grounding procedures.
Once the controller is connected to electricity and properly grounded, the sensors can be connected. Wiring can be completed for up to 42 stations using additional modules. After the valve wires are connected, the inner door assembly can be attached to the controller. Finally, connect the grey ribbon to the inner door assembly prior to turning the power back on to the controller.
When using a pedestal configuration, a base must be built using 2 x 4's, conduit, and concrete. Mount the pedestal to the slab using the metal base and hardware provided.